Australian Approved Product
The LED 18w T8 Lamp has the following features;
Australian Approved Product
Always switch off the power supply before installation.
Mirabella LED Tubes are intended for use in luminaires with conventional magnetic ballast with Starter.
Do not use Mirabella LED Tubes in luminaires with High Frequency Electronic ballast - No Starter.
Mirabella LED Tubes operate in temperature from -10 degree Celsius to 40 degree Celsius under dry conditions or in luminaires that provide correct protection.
Mirabella LED Tubes are not dimmable.
Mirabella LED Tubes are designed to fit IEC Compliant G13 bi-pin lamp holders.
All LED tubes must be installed by a professional electrician.
Do not change any componenets of the Mirabella LED Tubes.
The supplied warning sticker shall be placed on the luminaire and shall be visible during lamp replacement.
Mirabella Tubes are designed for use in luminaires with magnetic ballast where no modification is needed for the inside of luminaire. They can also be used in new LED luminaires with Direct AC-input
Tubes are not suited for emergency luminaires designed for double-capped flourescent lamp(s).
These instructions are for general installation and therefore Mirabella do not accept any liability for any works on the luminaires.
If the luminaire is modified it must be undertaken by a qualified electrician. Luminaire must work according to known standards after converting to LED.
The power supply should always be switched off before installation.
In case the luminaire is equipped with lighting control (for instance 0-10v dimmer) then the control wires for the lighting control should be removed.
When wires are changed they shall be replaced by new wires of a type (electric & thermal) that are suitable for the luminaire.
Wires in Class II luminaires shall only be replaced by wires of same type and quality.
Never install wires over sharp edges in the luminaire.
Class II luminaires must keep the same level and strength of insulation after conversion.
Connections to the ground (earth) may not be removed in the luminaire.
The IP rating of the luminaire may not be degraded after converison.
Any direct or indirect dmagaes that may occur during installation that is not performed according to this guide or by a qualified electrician is not under the liability of Mirabella.
Never change the structure of the Mirabella LED Tubes.
The overall energy efficiency and light distribution is determined by the design of the installation.
Incorrect installation may cause failure and other problems with the installation.
LED's are mercury free which means disposing of them can be done more safely
Not suitable for dimmers, electronic timers or electronic switching devices